Question about Electrical Supplies
Posted by Anonymous on
That model number is actually supported by Briggs & Stratton. The phone number to contact them for support is 1-800-274-4477.
Posted on Apr 21, 2019
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
If this is one of the big "taco cart" portables you need to check that the vent on the gas cap is open when you're running the engine. In the center of the gage on the gas cap is a little knurled knob, turn it counter clockwise (lefty loosey), about a half turn or so and run the generator.
If that doesn't solve your problem add to it here, otherwise please give me a rating I'm trying to build a little credibility here and could use the help.
Posted on Dec 02, 2008
the instructions says the voltage regulator is automatic/digital. when you check the voltage is there any load on the generator? if applying load to the generator doesn't help, you can manually change the motor speed where the governor connects to the carborator, but it may change the frequency, but the regulator may fix it
Posted on Apr 13, 2009
I am assuming the generator worked fine before the oil change. Now that you have done the oil change the genset does not start. These generators have a safety switch, which is basically an oil pressure switch that keeps the engine from running when there is not enough oil in the engine. Make sure that there is enough oil and if there is, look for a wire that runs along side of the engine to a round component. disconnect that wire and try starting. If it does not start then try to ground out the wire to the engine block. If this does not work, then there is other engine problems.
Posted on May 08, 2009
I have the 18KW model and was told that most alarms relate to a low battery. Make sure the battery charger in the Transfer Switch is properly feeding the battery or hook up a mobil battery charger to the battery and see if the alarm goes away. Good Luck.
Posted on Oct 12, 2009
Tips for a great answer:
Sep 18, 2017 | Generac Electrical Supplies
Jan 21, 2016 | Electrical Supplies
Dec 05, 2015 | Generac Electrical Supplies
Aug 28, 2015 | Electrical Supplies
Mar 17, 2015 | Generac Electrical Supplies
May 18, 2011 | Garden
Feb 23, 2011 | Generac Power Systems Generac 5522 14 Kw...
Jun 03, 2010 | Generac 100 Amp 120/240-Volt Transfer...
Apr 30, 2010 | Briggs Garden
223 people viewed this question
Usually answered in minutes!